| || ||Thread Tools||Search this Thread|
|27th February 2008, 21:11||#1|
Join Date: May 2007
Thanked: 13 Times
What is wrong with my UPS?
I have a Microtek Heritage+ 600 UPS. Whenever the electricity goes off, the generator kicks in after about 30 seconds or so. But the UPS goes into the red and continues to give beep sound. Isn't the UPS supposed to go back to the normal mode when the generator kicks in? After all, it should treat power as it is - whether it comes through the mains or the generator.
What's wrong with it? I am technically so please help.
|27th February 2008, 23:37||#3|
Join Date: Oct 2005
Thanked: 1,976 Times
I have a question. When your generator starts running have you tried putting in a tester in that plug point where the UPS is connected and see whether the power is available on that point?
Many a times the generators do not/can not supply power to the whole place. In such cases the wiring is done to keep the bare minimum things running. It is possible that the generators power never reaches that plug point.
|27th February 2008, 23:42||#4|
Join Date: Dec 2007
Location: Pondicherry, Chennai
Thanked: 0 Times
Assuming your UPS is in good health there are two reasons for this:
1. The genrator electricity and normal electricity is not the same. Generated electricity is more rough with huge fluctuations than the supplied electricity. If your UPS is really a good one it senses this rough load and cuts of the input electricity. But this will not happen in latest technology gensets as they have special equipments to smoothen the output power - but only very latest and technically advanced sets have this.
2. Normally many of the electrical appliances take more load to start than during the continuous running time. So the generated load during the initial few minutes would be less than sufficient if you are running too many appliances. This could also be a reason for the UPS to cut of the inpur power. Read the following to understand better:
"Electrical loads such as incandescent lamps and hot plates require the same wattage to start as is needed to maintain use.
Loads such as fluorescent lamps require 2 to 2 times the indicated wattage during start-up. Loads for mercury lamps require 2 to 3 times the indicated wattage during start-up.
Electrical motors require a large starting current. Power requirements depend on the type of motor and its use. Once enough "surge" is attained to start the motor, the appliance will require only 50% to 30% of the wattage to continue running.
Most electrical tools require 2 to 3 times their wattage for running under load during use. (For example, a 9,000 watt generator can power a 3,200 to 7,000 watt electrical tool.)
Loads such as submersible pumps, air conditioners and air compressors require a very large force to start. They need 3 to 5 times the normal running wattage in order to start. (For example, a 5,000 watt generator would only be able to drive a 1,800 to 3,100 watt pump.) "
Usually it is not advisable to run sensitive electronic items especially computers in generated power - better to have a long stand by UPS.
|27th February 2008, 23:47||#5|
Senior - BHPian
Join Date: Jul 2006
Thanked: 433 Times
|28th February 2008, 07:27||#6|
Join Date: Mar 2006
Thanked: 370 Times
|28th February 2008, 16:12||#7|
Join Date: Nov 2006
Thanked: 3,388 Times
In fact, a friend of mine whose apartments have generator backup told me that power is made available only to the lights and fans, and not to any power outlets. Yours could be the same case.
|Thread Tools||Search this Thread|
|Thread||Thread Starter||Forum||Replies||Last Post|
|Which UPS to buy ?||adityamunshi||Gadgets, Computers & Software||235||21st June 2017 12:58|
|APC UPS: Good Service EDIT: Now a bad service experience added as well||bblost||Gadgets, Computers & Software||52||14th March 2014 17:31|
|Maruti Suzuki ups car prices||windsurfer||The Indian Car Scene||2||4th February 2008 18:16|
|pics: so more follow ups||gemballa||Super-Cars & Imports in India||1||4th October 2005 20:56|
|Formula 1 line ups for 2006 ??||Badcheetah||Int'l Motorsport||32||3rd October 2005 18:04|